Page IV - 58 
Ventilation Design Handbook on Animal Research Facilities Using Static Microisolators 
Table 4.1.08 Tabular Variation of H 2 O and CO 2 with Day: Test 1, Lights Off 
Cage Group 
Day 
RH actual 
(percent) 
C0 2 
(g/hr/lOOg 
BW) 
h 2 o 
(g/ hr/ lOOg 
BW) 
1-4 (Desired 
1 
71.3 
1.06E+00 
1.22E+00 
RH = 
2 
66.1 
8.02E-01 
1.08E+00 
30 - 35 percent) 
3 
70.4 
8.20E-01 
9.46E-01 
4 
62.9 
1.01E+00 
8.24E-01 
5 
61.4 
8.54E-01 
7.85E-01 
6 
54.4 
7.52E-01 
8.54E-01 
7 
52.6 
1.00E+00 
8.08E-01 
8 
58.4 
1.03E+00 
7.09E-01 
9 
61.4 
6.06E-01 
6.97E-01 
10 
57.1 
7.61E-01 
7.30E-01 
5-8 
1 
69.7 
8.48E-01 
-6.01E-01 
(Desired RH = 
2 
84.8 
8.82E-01 
1.14E+00 
75 - 80 percent) 
3 
83.8 
8.98E-01 
7.92E-01 
4 
78.2 
7.86E-01 
8.20E-01 
5 
77.7 
1.04E+00 
5.31E-01 
6 
79.6 
1 .05E+00 
9.08E-01 
7 
76.3 
7.85E-01 
5.75E-01 
8 
81.1 
9.89E-01 
7.75E-01 
9 
83.4 
8.85E-01 
8.20E-01 
10 
80.6 
6.76E-01 
1 .09E+00 
9-12 
1 
68.0 
1.22E+00 
1 .48E+00 
(Desired RH = 
2 
67.7 
7.95E-01 
1.09E+00 
30 - 35 percent) 
3 
62.8 
9.99E-01 
8.89E-01 
4 
66.2 
7.69E-01 
8.49E-01 
5 
56.8 
6.95E-01 
1.17E+00 
6 
55.5 
8.86E-01 
8.58E-01 
7 
62.4 
9.44E-01 
8.26E-01 
8 
54.1 
7.12E-01 
7.40E-01 
9 
60.2 
7.98E-01 
5.83E-01 
10 
60.5 
7.97E-01 
7.44E-01 
