Page IV ~ 60 
Ventilation Design Handbook on Animal Research Facilities Using Static Microisolators 
Table 4.1.10 Tabular Variation of H 2 0 and C0 2 with Day; Desired RH = 30 - 35 percent, 
Lights Off 
Cage Group 
Day 
RH actual 
(percent) 
co 2 
(g/hr/lOOg 
BW) 
HiO 
(g/ hr/ lOOg 
BW) 
1-4 
1 
71.3 
1.06E+00 
1.22E+00 
Test 1 
2 
66.1 
8.02E-01 
1.08E+00 
3 
70.4 
8.20E-01 
9.46E-01 
4 
62.9 
1.01E+00 
8.24E-01 
5 
61.4 
8.54E-01 
7.85E-01 
6 
54.4 
7.52E-01 
8.54E-01 
7 
52.6 
1.00E+00 
8.08E-01 
8 
58.4 
1.03E+00 
7.09E-01 
9 
61.4 
6.06E-01 
6.97E-01 
10 
57.1 
7.61E-01 
7.30E-01 
9-12 
1 
68.0 
1.22E+00 
1.48E+00 
Test 1 
2 
67.7 
7.95E-01 
1.09E+00 
3 
62.8 
9.99E-01 
8.89E-01 
4 
66.2 
7.69E-01 
8.49E-01 
5 
56.8 
6.95E-01 
1.17E+00 
6 
55.5 
8.86E-01 
8.58E-01 
7 
62.4 
9.44E-01 
8.26E-01 
8 
54.1 
7.12E-01 
7.40E-01 
9 
60.2 
7.98E-01 
5.83E-01 
10 
60.5 
7.97E-01 
7.44E-01 
1-4 
1 
69.7 
9.86E-01 
1.03E+00 
Test 2 
2 
59.6 
9.92E-01 
1.10E+00 
3 
62.6 
9.76E-01 
8.73E-01 
4 
63.7 
9.71E-01 
8.60E-01 
5 
64.4 
7.90E-01 
7.93E-01 
6 
58.0 
8.04E-01 
8.99E-01 
7 
64.0 
1.02E+00 
6.48E-01 
8 
50.3 
8.80E-01 
7.40E-01 
9 
50.6 
7.58E-01 
9.49E-01 
10 
52.4 
7.65E-01 
5.78E-01 
