Volume I - Section IV - Experimental Work and Verification of CFD Methodology 
Page IV -81 
Table 4.2.03. Comparison of CFD results against Series Sets Two: Parallel Orientation, SF6 
Results 
Tunnel Velocity (FPM) 
Ventilation Rate (CFM) 
0.1 1/min SF 6 
Parallel - Heater On 
CFD 
Set Two 
20 
0.04 
0.04 
30 
0.05 
0.05 
40 
0.06 
0.06 
Table 4.2.04. Comparison of CFD results against Series Sets Two: Perpendicular Orientation, 
Heater On, SF6 Results 
Tunnel Velocity (FPM) 
Ventilation Rate (CFM) 
0.1 1/min SF 6 
Perpendicular - Heater On 
CFD 
Set Two 
20 
0.05 
0.04 
30 
0.05 
0.05 
40 
0.06 
0.05 
Table 4.2.05. Comparison of CFD results against Series Sets One and Three: Parallel 
Orientation, Heater On Results. 
Tunnel Velocity 
(FPM) 
Ventilation Rate (CFM) 
0.1 1/min C0 2 
Parallel - Heater On 
CFD 
Series Set One 
Series Set Three 
20 
0.07 
0.07 
0.08 
30 
0.09 
0.10 
0.11 
40 
0.10 
0.10 
0.13 
