Page IY - 82 
Ventilation Design Handbook on Animal Research Facilities Using Static Microisolators 
Table 4.2.06. Comparison of CFD results against Series Sets Three: Parallel Orientation, Heater 
Off Results. 
Tunnel Velocity 
(FPM) 
Ventilation Rate (CFM) 
0.1 1/min C0 2 
Parallel - Heater Off 
CFD 
Series Set Three 
Series Set Three 
(Repeat) 
20 
0.10 
0.09 
— 
30 
0.10 
0.12 
0.09* 
40 
0.12 
0.15 
— 
* The percent difference between the two separate experimental measurements is 
25 percent 
Table 4.2.07. Comparison of CFD results against Series Sets Three: Perpendicular Orientation, 
Heater On Results. 
Tunnel Velocity (FPM) 
Ventilation Rate (CFM) 
0.1 1/min C0 2 
Perpendicular - Heater On 
CFD 
Series Set Three 
20 
0.15 
0.08 
30 
0.18 
0.14 
40 
0.21 
0.24 
Table 4.2.08. Comparison of CFD results against Series Sets Three: Perpendicular Orientation, 
Heater Off Results. 
Tunnel Velocity (FPM) 
Ventilation Rate (CFM) 
0.1 1/min CO 2 
Perpendicular - Heater Off 
CFD 
Series Set Three 
20 
0.15 
0.06 
30 
0.18 
0.09 
40 
0.21 
0.17 
