Page IV - 104 
Ventilation Design Handbook on Animal Research Facilities Using Static Microisolators 
Fill 
Temperature 
77.000 
76.000 
75.000 
74 . 000 
73.000 
72 . 000 
71.000 
70.000 
Figure 4.74 Fill Plot of Temperature Field ( CFD ) at Plane 1 ( Plane 0.15m (6") from North 
Wall). Empty Room Case. 
Figure 4.75 Fill Plot of Temperature Field (CFD) at Plane 8 (Plane 1.22m (48”) from North 
Wall). Empty Room Case. 
