Page A I - 8 
Design Handbook on Animal Research Facilities Using Static Microisolators 
2.2 Experimental Data 
The experimental data sets for the cage condition section of work are summarized below: 
Series Set 
Tracer 
Gas 
Injection 
Rate 
(17 min) 
Sampling 
Method 
Mouse 
Heater 
Type 
Cage 
Orientation 
Tunnel 
Air 
Velocity 
Range 
(fpm) 
Base 
co 2 
1.0 
Steady 
DMH 
(On/ Off) 
Par, Perp, 
Vert 
15 - 100 
One 
co 2 
0.1 
Steady 
DMH 
(On only) 
Par, Perp 
15-50 
Two 
sf 6 
0.1 
Steady 
DMH 
(On only) 
Par, Perp 
15-50 
Three 
co 2 
0.1 
Steady 
DMH 
(On / Off) 
Par, Perp, 
Vert 
20, 40 
Four 
co 2 
0.1 
Steady 
SMO 
(On only) 
Par, Perp, 
Vert 
20, 30, 40 
Five 
co 2 
0.1 
Decay 
SMO 
(On only) 
Par, Perp, 
Vert 
20, 30, 40 
Six 
co 2 
0.1 
Steady 
DMH (On/ 
Off); SMO 
(On Only) 
Par, Perp 
20,40 
Seven 
co 2 
0.1 
Steady 
DMH (On/ 
Off); SMO 
(On Only) 
Par, Perp 
20, 40 
Eight 
co 2 
0.1 
Steady 
SMO (On 
Only) 
Par, Perp 
30 
