Page A I - 14 
Design Handbook on Animal Research Facilities Using Static Microisolators 
2.2.4 Series Set Three 
Parallel Cage Orientation: Heater On 
Desired Air Velocity (fpm) 
Temperature Rise in Cage (°F) 
Ventilation Rate (cfm) 
20 
3.90 
0.08 
30 
3.00 
0.11 
40 
5.45 
0.13 
Parallel Cage Orientation: Heater Off 
Desired Air Velocity (fpm) 
Temperature Rise in Cage (°F) 
Ventilation Rate (cfm) 
20 
2.16 
0.09 
30 
2.63 
0.12 
40 
1.97 
0.15 
Perpendicular Cage Orientation: Heater On 
Desired Air Velocity (fpm) 
Temperature Rise in Cage (°F) 
Ventilation Rate (cfm) 
20 
3.78 
0.08 
30 
4.45 
0.14 
40 
3.66 
0.24 
Perpendicular Cage Orientation: Heater Off 
Desired Air Velocity (fpm) 
Temperature Rise in Cage (°F) 
Ventilation Rate (cfm) 
20 
3.16 
0.06 
30 
2.37 
0.09 
40 
3.04 
0.17 
Vertical Cage Orientation: Heater On 
Desired Air Velocity (fpm) 
Temperature Rise in Cage (°F) 
Ventilation Rate (cfm) 
20 
6.36 
0.08 
30 
4.54 
0.09 
40 
5.66 
0.10 
Vertical Caee Orientation: 
Heater Off 
Desired Air Velocity (fpm) 
Temperature Rise in Cage (°F) 
Ventilation Rate (cfm) 
20 
4.04 
0.07 
30 
4.20 
0.07 
40 
4.95 
0.08 
