Page A I - 30 
Design Handbook on Animal Research Facilities Using Static Mieroisolators 
3.2 Calibration Procedures 
3.2.1 Calorimeter Approach Air Velocity Calibration: ( Calibration Data Prior to Test 
1 ) 
Calorimeter 
n 
72 
48 
50 
57 
66 
Av. = 
Air velocity = 
68 
51 
47 
56 
63 
(fpm) 
58 fpm 
74 
50 
52 
56 
59 
Voltage Regulated Setting = 64 
Calorimeter 
(#3 
55 
47 
51 
55 
59 
Av. = 
Air velocity = 
53 
44 
44 
50 
65 
(fpm) 
51 fpm 
58 
39 
38 
43 
58 
Voltage Regulated Setting = 61 
