Page A I - 60 
Design Handbook on Animal Research Facilities Using Static Microisolators 
Cage: 1 ,2,3,4 Calorimeter - 3 (desired RH 30-35 percent) 
Concentration 
Air 
low 
Actual temperature 
Time 
o 2 
(percent) 
co 2 
(percent) 
NH 3 (ppm) 
Scale 
Rate (1/min) 
Temp (°F) 
Temp(°C) 
Actual RH 
(percent) 
1 
20.4 
0.44 
30 
41 
4.39 
75.79 
24.33 
46.52 
2 
20.3 
0.44 
33 
41 
4.39 
75.44 
24.13 
49.97 
3 
20.3 
0.47 
31 
41 
4.39 
75.67 
24.26 
49.98 
Average 
20.3 
0.45 
31 
41 
4.39 
75.63 
24.24 
48.82 
4 
20.3 
0.75 
34 
44 
4.95 
74.87 
23.82 
53.89 
5 
20.1 
0.86 
36 
44 
4.95 
74.83 
23.79 
59.57 
6 
20.1 
0.93 
41 
44 
4.95 
76.01 
24.45 
61.83 
Average 
20.2 
0.85 
37 
44 
4.95 
75.24 
24.02 
58.43 
Mice weight=449.9 (g) 
Room (desired RH 35-40 percent) 
Concentration 
Airflow 
Actual temperature 
Time 
o 2 
(percent) 
co 2 
(percent) 
NH 3 (ppm) 
Scale 
Rate (1/min) 
Temp (°F) 
Temp(°C) 
Actual RH 
(percent) 
1 
20.6 
0.09 
3 
- 
- 
69.75 
20.97 
41.50 
2 
20.6 
0.09 
3 
- 
- 
71.16 
21.76 
41.21 
3 
20.6 
0.09 
5 
- 
- 
70.78 
21.54 
41.74 
Average 
20.6 
0.09 
4 
70.56 
21.42 
41.48 
4 
21.0 
0.05 
0 
- 
- 
70.84 
21.58 
42.13 
5 
21.0 
0.05 
1 
- 
- 
70.08 
21.16 
41.70 
6 
20.9 
0.06 
0 
- 
- 
71.99 
22.22 
40.82 
Average 
21.0 
0.05 
0 
70.97 
21.65 
41.55 
Date: OCT 26,1997 Day: 9 
Barometric pressure: 29.52 (in) Desired temperature: 24+-1.5 °C 
Desired airflow: 5 (1/min) 
Cage: 9,10,11,12 Calorimeter - 1 (desired RH 30-35 percent) 
Concentration 
Airflow 
Actual temperature 
Time 
o 2 
(percent) 
co 2 
(percent) 
NH 3 (ppm) 
Scale 
Rate (1/min) 
Temp (°F) 
Temp(°C) 
Actual RH 
(percent) 
1 
20.1 
0.55 
56 
41 
4.99 
- 
- 
52.10 
2 
20.1 
0.57 
56 
43 
5.26 
- 
- 
52.47 
3 
20.0 
0.60 
52 
43 
5.26 
- 
- 
53.94 
Average 
20.1 
0.57 
55 
42 
5.17 
52.84 
4 
20.1 
0.74 
99 
41 
4.99 
77.15 
25.08 
59.67 
5 
20.1 
0.74 
97 
41 
4.99 
76.90 
24.94 
59.30 
6 
20.1 
0.75 
97 
41 
4.99 
77.05 
25.03 
61.56 
Average 
20.1 
0.74 
98 
41 
4.99 
77.03 
25.02 
60.18 
Mice weight=47 1 .9 (g) 
