Page A I - 84 
Design Handbook on Animal Research Facilities Using Static Microisolators 
3. 4. 1.4 Individual Calorimeter Data ( O 2 percent, CO 2 percent, and NH3 ppm) for Test 2 
For cages: 1,2,3, 4 
Desired temperature: 24+-1.5 °C Desired humidity: 30-35 percent 
Lights on 
Day 
Calor. 
o 2 
(percent) 
co 2 
(percent) 
Tube 
nh 3 
(ppm) 
nh 3 
(ppm) 
Max 
nh 3 
(ppm) 
Airflow 
(1/min) 
Actual 
RH 
(percent) 
Temp. 
(°C) 
Bar. 
press 
(in) 
1 
1 
20.17 
0.63 
0 
0 
0 
4.98 
67.24 
22.23 
29.77 
2 
3 
19.97 
0.62 
0 
3 
3 
4.99 
60.60 
23.31 
29.77 
3 
2 
20.10 
0.55 
0 
2 
2 
5.01 
54.46 
24.80 
29.83 
4 
1 
20.10 
0.55 
1 
2 
2 
4.92 
57.10 
24.88 
30.06 
5 
3 
20.07 
- 
1 
10 
11 
5.08 
60.47 
24.21 
30.04 
6 
2 
20.00 
0.52 
4 
15 
18 
4.89 
51.85 
26.09 
29.83 
7 
1 
20.10 
0.50 
2 
10 
10 
5.93 
54.42 
24.05 
29.72 
8 
3 
20.30 
0.30 
2 
21 
28 
7.71 
46.63 
22.85 
29.92 
9 
2 
20.40 
0.23 
9 
9 
10 
9.05 
46.97 
23.64 
29.79 
10 
1 
20.33 
0.26 
12 
21 
30 
9.18 
48.33 
22.53 
29.72 
Light off 
Day 
Calor. 
o 2 
(percent) 
co 2 
(percent) 
Tube 
nh 3 
(ppm) 
nh 3 
(ppm) 
Max 
nh 3 
(ppm) 
Airflow 
(1/min) 
Actual 
RH 
(percent) 
Temp. 
(°C) 
Bar. 
press 
(in) 
1 
1 
20.00 
0.74 
0 
2 
2 
4.99 
69.74 
22.26 
29.77 
2 
3 
19.93 
0.76 
0 
0 
0 
4.97 
59.57 
23.56 
29.77 
3 
2 
19.93 
0.77 
0 
1 
2 
4.96 
62.64 
24.95 
29.86 
4 
1 
19.90 
0.80 
1 
6 
6 
4.89 
63.70 
25.14 
29.82 
5 
3 
19.70 
0.62 
2 
11 
12 
5.08 
64.44 
23.81 
30.04 
6 
2 
19.80 
0.66 
5 
21 
22 
4.92 
57.95 
24.82 
29.80 
7 
1 
20.03 
0.72 
2 
17 
24 
5.83 
64.04 
23.35 
29.83 
8 
3 
20.23 
0.47 
5 
- 
- 
7.74 
50.30 
22.93 
29.92 
9 
2 
20.27 
0.37 
11 
43 
54 
8.80 
50.61 
23.75 
29.79 
10 
1 
20.30 
0.36 
12 
31 
43 
9.18 
52.38 
22.60 
29.74 
