Page A I - 86 
Design Handbook on Animal Research Facilities Using Static Microisolators 
For cages: 9,10,11,12 
Desired temperature: 24+-1.5 °C Desired humidity: 75-80 percent 
Lights on 
Day 
Calor. 
o 2 
(percent) 
co 2 
(percent) 
Tube 
nh 3 
(ppm) 
nh 3 
(ppm) 
Max 
nh 3 
(ppm) 
Airflow 
(1/min) 
Actual 
RH 
(percent) 
Temp. 
(°C) 
Bar. 
press 
(in) 
1 
3 
20.07 
0.67 
0 
0 
0 
4.99 
73.03 
22.90 
29.77 
2 
2 
20.20 
0.63 
0 
4 
4 
5.02 
83.00 
23.09 
29.77 
3 
1 
20.07 
0.62 
0 
2 
2 
4.97 
82.87 
24.72 
29.83 
4 
3 
20.00 
0.60 
8 
2 
3 
5.11 
74.05 
23.69 
30.06 
5 
2 
19.93 
- 
57 
43 
47 
5.09 
77.25 
24.69 
30.04 
6 
1 
19.87 
0.47 
90 
105 
109 
5.03 
75.79 
24.96 
29.83 
7 
3 
20.03 
0.54 
86 
89 
92 
6.03 
72.58 
23.92 
29.72 
8 
2 
20.10 
0.33 
109 
139 
142 
7.64 
78.55 
23.72 
29.92 
9 
1 
20.20 
0.31 
120 
118 
122 
9.24 
79.03 
22.37 
29.79 
10 
3 
20.10 
0.42 
86 
95 
102 
9.09 
76.20 
23.02 
29.72 
Light off 
Day 
Calor. 
o 2 
(percent) 
co 2 
(percent) 
Tube 
nh 3 
(ppm) 
nh 3 
(ppm) 
Max 
nh 3 
(ppm) 
Airflow 
(1/min) 
Actual 
RH 
(percent) 
Temp. 
(°C) 
Bar. 
press 
(in) 
1 
3 
19.93 
0.75 
0 
2 
3 
4.91 
74.26 
23.01 
29.77 
2 
2 
19.73 
0.73 
0 
1 
1 
4.88 
80.43 
23.49 
29.77 
3 
1 
19.83 
0.88 
0 
1 
2 
4.89 
84.37 
25.41 
29.86 
4 
3 
19.73 
0.83 
10 
10 
12 
5.03 
79.44 
23.72 
29.82 
5 
2 
19.67 
0.68 
76 
65 
69 
4.96 
82.81 
24.82 
30.04 
6 
1 
19.80 
0.75 
105 
125 
132 
5.03 
81.10 
24.13 
29.80 
7 
3 
19.90 
0.74 
105 
147 
153 
6.03 
76.52 
23.66 
29.83 
8 
2 
20.03 
0.50 
126 
146 
153 
7.75 
76.81 
23.64 
29.92 
9 
1 
20.10 
0.45 
145 
130 
135 
9.18 
77.56 
22.43 
29.79 
10 
3 
20.07 
0.45 
96 
116 
128 
9.09 
81.03 
22.68 
29.74 
