Page A I - 140 
Design Handbook on Animal Research Facilities Using Static Microisolators 
4.3 Empty Room Data 
4.3.1 Surface Temperature and Ventilation System Data 
Data Files 
Zlup-e8 
to 
Zlup-el2 
Zlup-el 
to 
Zlup-e7 
Zlup-m8 
to 
Zlup- 
ml5 
Zlup-m4 
to 
Zlup-m7 
Zlup-ml 
to 
Zlup-m3 
Zlup-wl 
to 
Zlup-w7 
Zlup-w8 
to 
Zlup-wl5 
Room 
Surface 
Temp (F) 
Walls: 
South 
(Center) 
68 
68 
71 
70 
69 
70 
70 
West 
(Center) 
70 
69 
69 
70 
68 
70 
70 
North (East 
of Door) 
71 
70 
69 
69 
69 
70 
70 
North 
(West of 
Door) 
70 
69 
69 
70 
69 
70 
70 
East 
(Center) 
70 
69 
68 
70 
68 
70 
70 
Floor 
( Center) 
69 
69 
65 
68 
68 
69 
69 
Ceiling: 
South 
68 
68 
69 
69 
68 
70 
70 
West 
70 
69 
70 
70 
68 
70 
70 
North 
70 
70 
70 
70 
69 
70 
71 
East 
70 
69 
70 
68 
69 
70 
70 
Room 
Airflow 
(cfm) 
Supply Fan 
128 
128 
128 
128 
128 
129 
128 
Exhaust 
Fan 
102 
102 
105 
103 
103 
104 
103 
Pressure 
Difference 
(in. water) 
0.04 
0.04 
0.04 
0.04 
0.04 
0.04 
0.04 
Barometric 
Pressure 
(mm Hr) 
29.13 
29.03 
29.16 
29.13 
29.28 
29.38 
29.35 
