Page A I - 142 
Design Handbook on Animal Research Facilities Using Static Microisolators 
Data Files 
Z2nw-1 
to 
Z2nw-7 
Z2ne-1 
to 
Z2ne-7 
Z2nm-1 
to 
Z2nm-13 
Z3ex-nl5 
to nl6; si 
to s4 
Z3ex-nl to 
Z3ex-nl4 
Z3ex-s5 
to 
Z3ex-s7 
Z3ex-s8 
Room 
Surface 
Temp (F) 
Walls: 
South 
(Center) 
71 
70 
69 
70 
68 
68 
69 
West 
(Center) 
71 
70 
69 
70 
69 
69 
69 
North (East 
of Door) 
71 
71 
69 
70 
68 
68 
69 
North (West 
of Door) 
70 
70 
68 
70 
68 
69 
69 
East 
(Center) 
71 
71 
69 
70 
69 
68 
69 
Floor 
( Center) 
70 
70 
68 
69 
68 
68 
67 
Ceiling: 
South 
71 
70 
69 
70 
70 
68 
70 
West 
72 
70 
70 
71 
70 
69 
69 
North 
71 
71 
70 
71 
70 
69 
70 
East 
71 
71 
70 
70 
70 
70 
70 
Room 
Airflow (cfm) 
Supply Fan 
129 
129 
130 
129 
129 
129 
128 
Exhaust Fan 
96 
103 
98 
103 
103 
102 
102 
Pressure 
Difference 
(in. water) 
0.05 
0.04 
0.06 
0.04 
0.04 
0.04 
0.04 
Barometric 
Pressure 
(mm Hr) 
29.59 
28.87 
29.47 
29.06 
29.06 
29.05 
29.1 
