( 2 ) 
ST* 
i 
of water, the Tank to be covered in with 2” plarking, having 
a Draw off Cock fitted to Distribution Pipe. 
£J.?pHABGK, ^he Discharge Pipe from the Pump to the Storage lark to 
PIPE. 
be I'l Galvanized Iron, to be laid below the ground surface, in 
as direct a line as possible, Approx length 2 f 000 ft. 
DIS^HIBlJ^Jpj The water to be Distributed from the Storage Tank through a 
P ^ PIN G * 
1 M Galvanized Iron Pipe, to where required, Approx, length 2,000 
STAND 
BIBS- 
ft. 
Approx, number required 10, made of C.I. placed at Conven¬ 
ient Distances apart along the line of Distribution piping, haviig 
a Bib Cock on one side, and a Plug Cock and Hose Connection, 
without caps, on the other side, thus enabling Watering by hese 
or Bucket as may be desired. 
GENERAL. 
TIME. 
The v/hole of the workmanship and material to be of the 
best possible, all excavation work to be smoothed over aftex* 
all joints along the lines of piping have been inspected and 
found tight. 
6i 
The approximate time required to complete the whole of the 
work to be about 5 months from the date of order. 
The Contractor will hand over the v/hole plant to the 
Authorities after having run same for one month after completion. 
THE BORNEO COMPANY, LIMITED. 
