Z 1-. 
Pipilifr n* Galvanised § forty ( 40 cts ) coots per foot run laid in position# 
-do- § thirty- ( 30 cts) -do- 
—do— 
-do- 
With regard to above tender we would sug^nst ; Instead of enlarging; well which 
is a most expensive operation and almost impossible to estimate closely upon, in view of its 
close proximity to the lake »that it be only cleaned out and that the suction pipe from pump 
be carried into it and a branch from same carried to late so that if well should ran dry a 
supply could always be gpt direct from late* 
With this alteration! a reduction of Dollars On e thous and one hundre d ( $ 1,100; 00) 
could be made on Tender No.l . 
% 
TEND® ND*2 - As there will be practically no head of water with tank as in tender No.l 
and therefore no pressure of water at level of walk round Band Stand, we propose 
if a 10,000 (-alien capacity tank must be adhered to, that a re-inf orced concrete 
tank as shewn on Plan No # 6200 maited “Proposed Design" be built on the surface of 
the gground thereby giving; a head of roughly 0 feet when tank is full# 
Extra price on Tender No*l for this type of tank will be Dollars Two hundred and 
and ninety ( fl 290 ; 00 ) only# 
1ENIEE NO# 3 - To make effective use of a Sprayer on hose pipe we think that at . least 20 
feet head will be necessary at highest point and therefore propose a steel tank of 
5,000 gallons capacity placed on a Steel Tower 15 feet high to design as shewn on 
/ ' / 
Plan No.6199# ' 
The additional price for this type of tank to Tender No#l would be Dollars Four hundred 
and fifty ( # 450 • 00 ) only. 
4 
