92 PRELIMINARY REPORT ON COAL-TESTING PLANT, [btjll.2$ 
Coal consumed, pounds per hour. 
Coal consumed in producer 350 
Dry coal consumed in producer 323. 2 
Combustible consumed in producer 289. 3 
Equivalent coal used by producer plant 386 
Equivalent dry coal used by producer plant 356. 7 
Equivalent combustible used by producer plant 319. 1 
British thermal units. 
Per pound of coal as fired 12, 046 
Per pound of dry coal 13, 041 
Per pound of combustible 14, 560 
Per cubic foot of standard gas 154. jj 
From standard gas per pound dry coal burned in producer 8, 330 
From standard gas per hour per brake horsepower 11, 460 
Gas produced, cubic feet (reduced to standard). 
Total 522, 350 
Per hour 17, 412 
Per pound coal consumed in producer 4V). \ 
Per pound dry coal consumed in producer 53. 5 
Per pound combustible consumed in producer 60. 1 
Per pound equivalent coal used by producer plant 45. ; 
Per pound equivalent dry coal used by producer plant 48. }\ 
Per pound equivalent combustible used by producer pant 54. . 
Horsepower developed. 
Average electrical horsepower available for outside purposes 192. 
Average electrical horsepower developed at switch board 1 99. 
Average brake horsepower f available for outside purposes 226; 
Average brake horsepower f developed at engine 235 
Coal consumed in producer, pounds per horsepower per hour. 
Per electrical horsepower available for outside purposes.. 
Per electrical horsepower developed at switch board 
Per brake horsepower! available for outside purposes 
Per brake horsepower! developed at engine 
Equivalent pounds used by producer plant per electrical 
horsepower available for outside purposes j 
Equivalent pounds used by producer plant per electrical I 
horsepower developed at switch board j 
Equivalent pounds used by producer plant per brake 
horsepower! available for outside purposes . 
Coal as 
fired. 
Equivalent pounds used by producer plant per brake 
horsepower! developed at engine 
1.82 
1.75 
1 . 54 
1.49 
2.01 
1.93 
1. 70 
1.64 
Dry coal. 
1.68 
1 . 62 
1 . 43 
1 . 38 
1 . 85 
1.79 
1. 58 
1.52 
Combr 
til. ltv 
; I'.asni on .in assumed crticiriicy of 85 per cenl for generator and belt. 
