;knald] PRODUCER-GAS TESTS. l J5 
Coal consumed, pounds per hour. 
)al consumed in producer 394.5 
ry coal consumed in producer :>45). 3 
i>mbustible consumed in producer 309. 5 
equivalent coal used by producer plant 4H4. 6 
univalent dry coal used by producer plant 384. 8 
Equivalent combustible used by producer plant :>41 . () 
British thermal units. 
?r pound of coal as fired LI, 534 
*r pound of dry coal 13, 037 
3r pound of combustible 14, 720 
>r cubic foot of standard gas 1 53. 7 
com standard gas per pound dry coal burned in producer 7,730 
rom standard gas per hour per brake horsepower 11, 480 
Gas produced, cubic feet [reduced to standard). 
)tal 521, 100 
r hour 17, 560 
r pound coal consumed in producer 44. 5 
>r pound dry coal consumed in producer 50. 3 
sr pound combustible consumed in producer 56. 7 
r pound equivalent coal used 1 >y producer plant 40. 4 
r pound equivalent dry coal used by producer plant 45. 6 
r pound equivalent combustible used by producer plant 51.5 
Horsepower developed. 
'erage electrical horsepower available for outside purposes 1 88. 3 
'erage electrical horsepower developed at switch board 1 99. 9 
erage brake horsepower* available for outside purposes 221. 5 
erage brake horsepower* developed at engine 235 
Coal consumed in producer, pounds per horsepower per hour. 
[electrical horsepower available for outside purposes. . 
electrical horsepower developed at switch board 
brake horsepower* available for outside purposes 
\ brake horsepower* developed at engine 
jaivalent pounds used by producer plant per electrical 
orsepower available for outside purposes 
livalent pounds used by producer plant per electrical 
orsepower developed at switch board 
livalent pounds used by producer plant per brake 
orsepower* available for outside purposes 
d livalent pounds used by producer plant per brake 
1 orsepower* developed at engine 
Coal as 
fired. 
2.10 
1.97 
1 . 78 
1 . 68 
2.81 
2. 17 
L.96 
1 . 85 
Dry coal. 
1.86 
1. 75 
1.58 
L.49 
2. 04 
1 . 93 
1.71 
1.64 
Combus- 
tible. 
L.64 
1. 55 
1.40 
L.32 
I. si 
1.71 
1.54 
1.45 
: Based on an assumed efficiency of 85 per cenl for generator and belt. 
