SERVICE SUGGESTIONS 
Foreign matter in the water may accumulate on 
the seat and cause improper seating or sticking of 
the valve. 
When this condition arises the valve may be 
taken apart, without removing the body from the 
line, and may be cleaned as follows: 
1. Close hand valve. 
2. If necessary remove conduit connections. 
3. With a wrench loosen the clamp nut (1)). 
4. Lift coil assembly off of valve body. 
5. Remove valve seat (9) with a proper size AHN 
socket wrench and clean thoroughly. = 
6. Remove all foreign matter from the valve 
body (6) and valve stem. 
If the valve body is removed from the line, the 
inside parts may be flushed with pure naphtha. 
CAUTION: Highly inflammable. Z A REMOVABLE 
7. Replace valve seat. . AM SEAT 
8. Replace plunger (5) in coil (1). 
9. Replace entire assembly over valve body and 
tighten clamp nut. 
FELRERER 
"ee eeeen 
soststonetel 
5 
Patera 
0050, 
eta 
Oy 
eg 
ees 
vat 
RS 
segtgmnenets 
<5 
SS 
rw 
<5 xx 
RRR 
SOO 
ay, 
3S 
mois 550505 
0,0, 0,08, 
torn 
Sm UU 
45 
SICKO 
SOKO 
OS 
Methane 
} Sl SSS 
550 
0505 
10. Test the operation of the valve after re- Fig oInternsltcanatrictioniet Ty oe4375 
assembling. and V837A Valves. 
M.H.R. PRINTED IN U.S.A. 
PAGE 
